A data center (American English)  or data centre (British English) is a building or facility used to house computer systems and associated components, such as telecommunications and storage systems. It generally includes redundant or backup components and infrastructure for power supply, data communications connections, environmental controls (e.g. air conditioning, fire suppression) and various security devices. A large data center is an industrial-scale operation using as much electricity as a small town.
- 1 History
- 2 Requirements for modern data centers
- 3 Data center levels and tiers
- 4 Data center design
- 5 Energy use
- 6 Network infrastructure
- 7 Offsite backup storage
- 8 Applications
- 9 Top data centers and service providers worldwide
- 10 See also
- 11 References
- 12 External links
Data centers have their roots in the huge computer rooms of the 1940s, typified by ENIAC, one of the earliest examples of a data center. Early computer systems, complex to operate and maintain, required a special environment in which to operate. Many cables were necessary to connect all the components, and methods to accommodate and organize these were devised such as standard racks to mount equipment, raised floors, and cable trays (installed overhead or under the elevated floor). A single mainframe required a great deal of power, and had to be cooled to avoid overheating. Security became important – computers were expensive, and were often used for military purposes. Basic design-guidelines for controlling access to the computer room were therefore devised.
During the boom of the microcomputer industry, and especially during the 1980s, users started to deploy computers everywhere, in many cases with little or no care about operating requirements. However, as information technology (IT) operations started to grow in complexity, organizations grew aware of the need to control IT resources. The advent of Unix from the early 1970s led to the subsequent proliferation of freely available Linux-compatible PC operating-systems during the 1990s. These were called "servers", as timesharing operating systems like Unix rely heavily on the client-server model to facilitate sharing unique resources between multiple users. The availability of inexpensive networking equipment, coupled with new standards for network structured cabling, made it possible to use a hierarchical design that put the servers in a specific room inside the company. The use of the term "data center", as applied to specially designed computer rooms, started to gain popular recognition about this time.
The boom of data centers came during the dot-com bubble of 1997–2000. Companies needed fast Internet connectivity and non-stop operation to deploy systems and to establish a presence on the Internet. Installing such equipment was not viable for many smaller companies. Many companies started building very large facilities, called Internet data centers (IDCs), which provide commercial clients with a range of solutions for systems deployment and operation. New technologies and practices were designed to handle the scale and the operational requirements of such large-scale operations. These practices eventually migrated toward the private data centers, and were adopted largely because of their practical results. Data centers for cloud computing are called cloud data centers (CDCs). But nowadays, the division of these terms has almost disappeared and they are being integrated into the term "data center".
With an increase in the uptake of cloud computing, business and government organizations scrutinize data centers to a higher degree in areas such as security, availability, environmental impact and adherence to standards. Standards documents from accredited professional groups, such as the Telecommunications Industry Association, specify the requirements for data-center design. Well-known operational metrics for data-center availability can serve to evaluate the commercial impact of a disruption. Development continues in operational practice, and also in environmentally-friendly data-center design. Data centers typically cost a lot to build and to maintain.
Requirements for modern data centers
IT operations are a crucial aspect of most organizational operations around the world. One of the main concerns is business continuity; companies rely on their information systems to run their operations. If a system becomes unavailable, company operations may be impaired or stopped completely. It is necessary to provide a reliable infrastructure for IT operations, in order to minimize any chance of disruption. Information security is also a concern, and for this reason a data center has to offer a secure environment which minimizes the chances of a security breach. A data center must therefore keep high standards for assuring the integrity and functionality of its hosted computer environment. This is accomplished through redundancy of mechanical cooling and power systems (including emergency backup power generators) serving the data center along with fiber optic cables.
The Telecommunications Industry Association's Telecommunications Infrastructure Standard for Data Centers specifies the minimum requirements for telecommunications infrastructure of data centers and computer rooms including single tenant enterprise data centers and multi-tenant Internet hosting data centers. The topology proposed in this document is intended to be applicable to any size data center.
Telcordia GR-3160, NEBS Requirements for Telecommunications Data Center Equipment and Spaces, provides guidelines for data center spaces within telecommunications networks, and environmental requirements for the equipment intended for installation in those spaces. These criteria were developed jointly by Telcordia and industry representatives. They may be applied to data center spaces housing data processing or Information Technology (IT) equipment. The equipment may be used to:
- Operate and manage a carrier's telecommunication network
- Provide data center based applications directly to the carrier's customers
- Provide hosted applications for a third party to provide services to their customers
- Provide a combination of these and similar data center applications
Effective data center operation requires a balanced investment in both the facility and the housed equipment. The first step is to establish a baseline facility environment suitable for equipment installation. Standardization and modularity can yield savings and efficiencies in the design and construction of telecommunications data centers.
Standardization means integrated building and equipment engineering. Modularity has the benefits of scalability and easier growth, even when planning forecasts are less than optimal. For these reasons, telecommunications data centers should be planned in repetitive building blocks of equipment, and associated power and support (conditioning) equipment when practical. The use of dedicated centralized systems requires more accurate forecasts of future needs to prevent expensive over construction, or perhaps worse — under construction that fails to meet future needs.
The "lights-out" data center, also known as a darkened or a dark data center, is a data center that, ideally, has all but eliminated the need for direct access by personnel, except under extraordinary circumstances. Because of the lack of need for staff to enter the data center, it can be operated without lighting. All of the devices are accessed and managed by remote systems, with automation programs used to perform unattended operations. In addition to the energy savings, reduction in staffing costs and the ability to locate the site further from population centers, implementing a lights-out data center reduces the threat of malicious attacks upon the infrastructure.
There is a trend to modernize data centers in order to take advantage of the performance and energy efficiency increases of newer IT equipment and capabilities, such as cloud computing. This process is also known as data center transformation.
Organizations are experiencing rapid IT growth but their data centers are aging. Industry research company International Data Corporation (IDC) puts the average age of a data center at nine years old. Gartner, another research company, says data centers older than seven years are obsolete. The growth in data (163 zettabytes by 2025) is one factor driving the need for data centers to modernize.
Data center transformation takes a step-by-step approach through integrated projects carried out over time. This differs from a traditional method of data center upgrades that takes a serial and siloed approach. The typical projects within a data center transformation initiative include standardization/consolidation, virtualization, automation and security.
- Standardization/consolidation: The purpose of this project is to reduce the number of data centers a large organization may have. This project also helps to reduce the number of hardware, software platforms, tools and processes within a data center. Organizations replace aging data center equipment with newer ones that provide increased capacity and performance. Computing, networking and management platforms are standardized so they are easier to manage.
- Virtualize: There is a trend to use IT virtualization technologies to replace or consolidate multiple data center equipment, such as servers. Virtualization helps to lower capital and operational expenses, and reduce energy consumption. Virtualization technologies are also used to create virtual desktops, which can then be hosted in data centers and rented out on a subscription basis. Data released by investment bank Lazard Capital Markets reports that 48 percent of enterprise operations will be virtualized by 2012. Gartner views virtualization as a catalyst for modernization.
- Automating: Data center automation involves automating tasks such as provisioning, configuration, patching, release management and compliance. As enterprises suffer from few skilled IT workers, automating tasks make data centers operations more efficient.
- Securing: In modern data centers, the security of data on virtual systems is integrated with existing security of physical infrastructures. The security of a modern data center must take into account physical security, network security, and data and user security.
The term "Machine Room" is at times used to refer to the large room within a Data Center where the actual Central Processing Unit is located; this may be separate from where high-speed printers are located. Air conditioning is most important in the machine room.
Aside from air-conditioning, there must be monitoring equipment, one type of which is to detect water prior to flood-level situations. One company, for several decades, has had share-of-mind: Water Alert. The company, as of 2018, has 2 competing manufacturers (Invetex, Hydro-Temp) and 3 competing distributors (Longden,Northeast Flooring,, Slayton).
Although the first raised floor computer room was made by IBM in 1956, and they've "been around since the 1960s," it was the 1970s that made it more common for computer centers to thereby allow cool air to circulate more efficienctly.
The first purpose of the raised floor was to allow access for wiring.
Data center levels and tiers
Telecommunications Industry Association
The Telecommunications Industry Association is a trade association accredited by ANSI (American National Standards Institute). In 2005 it published ANSI/TIA-942, Telecommunications Infrastructure Standard for Data Centers, which defined four levels of data centers in a thorough, quantifiable manner. TIA-942 was amended in 2008, 2010, 2014 and 2017.
The simplest requirements for the data center infrastructure is a Level 1 data center, which is basically a server room, following basic guidelines for the installation of computer systems. The most stringent level is a Level 4 data center, which is designed to host the most mission critical computer systems, with fully redundant subsystems, the ability to continuously operate for an indefinite period of time during primary power outages.
Data availability is a term used by computer storage manufacturers and storage service providers (SSPs) to describe products and services that ensure that data continues to be available at a required level of performance in situations ranging from normal through "disastrous."
Any time a server loses power, for example, it has to reboot, recover data and repair corrupted data. The time it takes to recover, known as the mean time to recover (MTR), could be minutes, hours or days.
Uptime Institute - Data Center Tier Standards
Four tiers are define by the Uptime Institute:
- Tier I: lacks redundant IT equipment, with 99.671% availability, maximum of 1729 minutes annual downtime
- Tier II: adds redundant infrastructure - 99.741% availability (1361 minutes)
- Tier III: adds more data paths, duplicate equipment, and that all IT equipment must be dual-powered (99.982%, 95 minutes)
- Tier IV: * All cooling equipment is independently dual-powered; adds Fault-tolerance (99.995%, 26 minutes)
Data center design
The field of data center design has been growing for decades in various directions:
- Major data centers did not appear in India until the late 1990s.
- a 65 story data center has already been proposed
- the number of data centers as of 2016 had grown beyond 3 million USA-wide, and more than triple
that number worldwide
Local building codes may govern the minimum ceiling heights and other parameters. Some of the considerations in the design of data centers are:
- size - one room of a building, one or more floors, or an entire building, and can hold 1,000 or more servers
- space, power, cooling, and costs in the data center.
- Mechanical engineering infrastructure - heating, ventilation and air conditioning (HVAC); humidification and dehumidification equipment; pressurization.
- Electrical engineering infrastructure design - utility service planning; distribution, switching and bypass from power sources; uninterruptible power source (UPS) systems; and more.
The higher the availability needs of a data center, the higher the capital and operational costs of building and managing it. Business needs should dictate the level of availability required and should be evaluated based on characterization of the criticality of IT systems estimated cost analyses from modeled scenarios. In other words, how can an appropriate level of availability best be met by design criteria to avoid financial and operational risks as a result of downtime? If the estimated cost of downtime within a specified time unit exceeds the amortized capital costs and operational expenses, a higher level of availability should be factored into the data center design. If the cost of avoiding downtime greatly exceeds the cost of downtime itself, a lower level of availability should be factored into the design.
Aspects such as proximity to available power grids, telecommunications infrastructure, networking services, transportation lines and emergency services can affect costs, risk, security and other factors to be taken into consideration for data center design. Whilst a wide array of location factors are taken into account (e.g. flight paths, neighbouring uses, geological risks) access to suitable available power is often the longest lead time item. Location affects data center design also because the climatic conditions dictate what cooling technologies should be deployed. In turn this impacts uptime and the costs associated with cooling. For example, the topology and the cost of managing a data center in a warm, humid climate will vary greatly from managing one in a cool, dry climate.
Modularity and flexibility
Modularity and flexibility are key elements in allowing for a data center to grow and change over time. Data center modules are pre-engineered, standardized building blocks that can be easily configured and moved as needed.
A modular data center may consist of data center equipment contained within shipping containers or similar portable containers. But it can also be described as a design style in which components of the data center are prefabricated and standardized so that they can be constructed, moved or added to quickly as needs change.
The physical environment of a data center is rigorously controlled. Air conditioning is used to control the temperature and humidity in the data center. ASHRAE's "Thermal Guidelines for Data Processing Environments" recommends a temperature range of 18–27 °C (64–81 °F), a dew point range of −9 to 15 °C (16 to 59 °F), and ideal relative humidity of 60%, with an allowable range of 40% to 60% for data center environments. The temperature in a data center will naturally rise because the electrical power used heats the air. Unless the heat is removed, the ambient temperature will rise, resulting in electronic equipment malfunction. By controlling the air temperature, the server components at the board level are kept within the manufacturer's specified temperature/humidity range. Air conditioning systems help control humidity by cooling the return space air below the dew point. Too much humidity, and water may begin to condense on internal components. In case of a dry atmosphere, ancillary humidification systems may add water vapor if the humidity is too low, which can result in static electricity discharge problems which may damage components. Subterranean data centers may keep computer equipment cool while expending less energy than conventional designs.
Modern data centers try to use economizer cooling, where they use outside air to keep the data center cool. At least one data center (located in Upstate New York) will cool servers using outside air during the winter. They do not use chillers/air conditioners, which creates potential energy savings in the millions. Increasingly indirect air cooling is being deployed in data centers globally which has the advantage of more efficient cooling which lowers power consumption costs in the data center. Many newly constructed data centers are also using Indirect Evaporative Cooling (IDEC) units as well as other environmental features such as sea water to minimize the amount of energy needed to cool the space.
Telcordia NEBS: Raised Floor Generic Requirements for Network and Data Centers, GR-2930 presents generic engineering requirements for raised floors that fall within the strict NEBS guidelines.
There are many types of commercially available floors that offer a wide range of structural strength and loading capabilities, depending on component construction and the materials used. The general types of raised floors include stringer, stringerless, and structural platforms, all of which are discussed in detail in GR-2930.
This design permits equipment to be fastened directly to the platform without the need for toggle bars or supplemental bracing. Structural platforms may or may not contain panels or stringers.
Data centers typically have raised flooring made up of 60 cm (2 ft) removable square tiles. The trend is towards 80–100 cm (31–39 in) void to cater for better and uniform air distribution. These provide a plenum for air to circulate below the floor, as part of the air conditioning system, as well as providing space for power cabling.
Raised floors and other metal structures such as cable trays and ventilation ducts have caused many problems with zinc whiskers in the past, and likely are still present in many data centers. This happens when microscopic metallic filaments form on metals such as zinc or tin that protect many metal structures and electronic components from corrosion. Maintenance on a raised floor or installing of cable etc. can dislodge the whiskers, which enter the airflow and may short circuit server components or power supplies, sometimes through a high current metal vapor plasma arc. This phenomenon is not unique to data centers, and has also caused catastrophic failures of satellites and military hardware.
To prevent single points of failure, all elements of the electrical systems, including backup systems, are typically fully duplicated, and critical servers are connected to both the "A-side" and "B-side" power feeds. This arrangement is often made to achieve N+1 redundancy in the systems. Static transfer switches are sometimes used to ensure instantaneous switchover from one supply to the other in the event of a power failure.
Low-voltage cable routing
Data cabling is typically routed through overhead cable trays in modern data centers. But some[who?] are still recommending under raised floor cabling for security reasons and to consider the addition of cooling systems above the racks in case this enhancement is necessary. Smaller/less expensive data centers without raised flooring may use anti-static tiles for a flooring surface. Computer cabinets are often organized into a hot aisle arrangement to maximize airflow efficiency.
Data centers feature fire protection systems, including passive and Active Design elements, as well as implementation of fire prevention programs in operations. Smoke detectors are usually installed to provide early warning of a fire at its incipient stage.
Two water-based options are
- No water - some of the benefits of using chemical suppression (clean agent fire suppression gaseous system).
Physical security also plays a large role with data centers. Physical access to the site is usually restricted to selected personnel, with controls including a layered security system often starting with fencing, bollards and mantraps. Video camera surveillance and permanent security guards are almost always present if the data center is large or contains sensitive information on any of the systems within. The use of finger print recognition mantraps is starting to be commonplace.
Documenting access is required by some data protection regulations. To do so, some organizations use access control systems that provide a logging report of accesses. Logging can occur at the main entrance, at the entrances to mechanical rooms and white spaces, as well as in at the equipment cabinets. Modern access control at the cabinet allows for integration with intelligent power distribution units so that the locks can be powered and networked through the same appliance.
Energy use is a central issue for data centers. Power draw for data centers ranges from a few kW for a rack of servers in a closet to several tens of MW for large facilities. Some facilities have power densities more than 100 times that of a typical office building. For higher power density facilities, electricity costs are a dominant operating expense and account for over 10% of the total cost of ownership (TCO) of a data center. By 2012 the cost of power for the data center is expected to exceed the cost of the original capital investment.
According to a Greenpeace study, in 2012, data centers represented 21% of the electricity consumed by the IT sector, which was about 382 billion kWh a year. U.S. data centers use more than 90 billion kWh of electricity a year. Global data centers used roughly 416 TWh in 2016, nearly 40% more than the entire United Kingdom.
Greenhouse gas emissions
In 2007 the entire information and communication technologies or ICT sector was estimated to be responsible for roughly 2% of global carbon emissions with data centers accounting for 14% of the ICT footprint. The US EPA estimates that servers and data centers are responsible for up to 1.5% of the total US electricity consumption, or roughly .5% of US GHG emissions, for 2007. Given a business as usual scenario greenhouse gas emissions from data centers is projected to more than double from 2007 levels by 2020.
Siting is one of the factors that affect the energy consumption and environmental effects of a datacenter. In areas where climate favors cooling and lots of renewable electricity is available the environmental effects will be more moderate. Thus countries with favorable conditions, such as: Canada, Finland, Sweden, Norway  and Switzerland, are trying to attract cloud computing data centers.
In an 18-month investigation by scholars at Rice University's Baker Institute for Public Policy in Houston and the Institute for Sustainable and Applied Infodynamics in Singapore, data center-related emissions will more than triple by 2020. 
The most commonly used metric to determine the energy efficiency of a data center is power usage effectiveness, or PUE. This simple ratio is the total power entering the data center divided by the power used by the IT equipment.
Total facility power consists of power used by IT equipment plus any overhead power consumed by anything that is not considered a computing or data communication device (i.e. cooling, lighting, etc.). An ideal PUE is 1.0 for the hypothetical situation of zero overhead power. The average data center in the US has a PUE of 2.0, meaning that the facility uses two watts of total power (overhead + IT equipment) for every watt delivered to IT equipment. State-of-the-art data center energy efficiency is estimated to be roughly 1.2. Some large data center operators like Microsoft and Yahoo! have published projections of PUE for facilities in development; Google publishes quarterly actual efficiency performance from data centers in operation.
The U.S. Environmental Protection Agency has an Energy Star rating for standalone or large data centers. To qualify for the ecolabel, a data center must be within the top quartile of energy efficiency of all reported facilities. The United States passed the Energy Efficiency Improvement Act of 2015, which requires federal facilities — including data centers — to operate more efficiently. In 2014, California enacted title 24 of the California Code of Regulations, which mandates that every newly constructed data center must have some form of airflow containment in place, as a measure to optimize energy efficiency.
European Union also has a similar initiative: EU Code of Conduct for Data Centres
Energy use analysis
Often, the first step toward curbing energy use in a data center is to understand how energy is being used in the data center. Multiple types of analysis exist to measure data center energy use. Aspects measured include not just energy used by IT equipment itself, but also by the data center facility equipment, such as chillers and fans. Recent research has shown the substantial amount of energy that could be conserved by optimizing IT refresh rates and increasing server utilization.
Power and cooling analysis
Power is the largest recurring cost to the user of a data center. A power and cooling analysis, also referred to as a thermal assessment, measures the relative temperatures in specific areas as well as the capacity of the cooling systems to handle specific ambient temperatures. A power and cooling analysis can help to identify hot spots, over-cooled areas that can handle greater power use density, the breakpoint of equipment loading, the effectiveness of a raised-floor strategy, and optimal equipment positioning (such as AC units) to balance temperatures across the data center. Power cooling density is a measure of how much square footage the center can cool at maximum capacity. The cooling of data centers is the second largest power consumer after servers. The cooling energy varies from 10% of the total energy consumption in the most efficient data centers and goes up to 45% in standard air-cooled data centers.
Energy efficiency analysis
An energy efficiency analysis measures the energy use of data center IT and facilities equipment. A typical energy efficiency analysis measures factors such as a data center's power use effectiveness (PUE) against industry standards, identifies mechanical and electrical sources of inefficiency, and identifies air-management metrics. However, the limitation of most current metrics and approaches is that they do not include IT in the analysis. Case studies have shown that by addressing energy efficiency holistically in a data center, major efficiencies can be achieved that are not possible otherwise.
Computational fluid dynamics (CFD) analysis
This type of analysis uses sophisticated tools and techniques to understand the unique thermal conditions present in each data center—predicting the temperature, airflow, and pressure behavior of a data center to assess performance and energy consumption, using numerical modeling. By predicting the effects of these environmental conditions, CFD analysis in the data center can be used to predict the impact of high-density racks mixed with low-density racks and the onward impact on cooling resources, poor infrastructure management practices and AC failure or AC shutdown for scheduled maintenance.
Thermal zone mapping
Thermal zone mapping uses sensors and computer modeling to create a three-dimensional image of the hot and cool zones in a data center.
This information can help to identify optimal positioning of data center equipment. For example, critical servers might be placed in a cool zone that is serviced by redundant AC units.
Green data centers
Data centers use a lot of power, consumed by two main usages: the power required to run the actual equipment and then the power required to cool the equipment. The first category is addressed by designing computers and storage systems that are increasingly power-efficient. To bring down cooling costs data center designers try to use natural ways to cool the equipment. Many data centers are located near good fiber connectivity, power grid connections and also people-concentrations to manage the equipment, but there are also circumstances where the data center can be miles away from the users and don't need a lot of local management. Examples of this are the 'mass' data centers like Google or Facebook: these DC's are built around many standardized servers and storage-arrays and the actual users of the systems are located all around the world. After the initial build of a data center staff numbers required to keep it running are often relatively low: especially data centers that provide mass-storage or computing power which don't need to be near population centers.Data centers in arctic locations where outside air provides all cooling are getting more popular as cooling and electricity are the two main variable cost components.
The practice of cooling data centers is a topic of discussion. It is very difficult to reuse the heat which comes from air cooled data centers. For this reason, data center infrastructures are more often equipped with heat pumps. An alternative to heat pumps is the adoption of liquid cooling throughout a data center. Different liquid cooling techniques are mixed and matched to allow for a fully liquid cooled infrastructure which captures all heat in water. Different liquid technologies are categorised in 3 main groups, Indirect liquid cooling (water cooled racks), Direct liquid cooling (direct-to-chip cooling) and Total liquid cooling (complete immersion in liquid). This combination of technologies allows the creation of a thermal cascade as part of temperature chaining scenarios to create high temperature water outputs from the data center.
Communications in data centers today are most often based on networks running the IP protocol suite. Data centers contain a set of routers and switches that transport traffic between the servers and to the outside world which are connected according to the data center network architecture. Redundancy of the Internet connection is often provided by using two or more upstream service providers (see Multihoming).
Some of the servers at the data center are used for running the basic Internet and intranet services needed by internal users in the organization, e.g., e-mail servers, proxy servers, and DNS servers.
Network security elements are also usually deployed: firewalls, VPN gateways, intrusion detection systems, etc. Also common are monitoring systems for the network and some of the applications. Additional off site monitoring systems are also typical, in case of a failure of communications inside the data center.
Offsite backup storage
Data centers are also used for off site backups. Companies may subscribe to backup services provided by a data center. This is often used in conjunction with backup tapes. Backups can be taken off servers locally on to tapes. However, tapes stored on site pose a security threat and are also susceptible to fire and flooding. Larger companies may also send their backups off site for added security. This can be done by backing up to a data center. Encrypted backups can be sent over the Internet to another data center where they can be stored securely.
Data backup techniques includes having a copy of the data offsite. Methods used for transporting data are:
- having the customer write the data to a physical medium, such as magnetic tape, and then transporting the tape elsewhere
- directly transferring the data to another site during the backup, using appropriate links
- uploading the data "into the cloud"
Top data centers and service providers worldwide
According to Cloudscene’s Leaderboard for Q1 2018, data center operators are ranked “based on both data center density (total operated data centers)", as well as "the number of listed service providers in the facility". Cloud service providers are ranked based on "connectivity (the total number of PoPs) for the region.” Chosen from a pool of more than 6,000 providers, the rankings are as follows:
- Q1, 2018 Top Data Center Operators Worldwide
- Q1, 2018 Top Service Providers Worldwide
|1||Zayo||Colt Technology Services||Telstra||Colt Technology Services|
|2||Level 3 Communications||EuNetworks||Vocus Communications||PCCW Solutions|
|3||Verizon||Cogent Communications||PIPE Networks||Tata Communications|
|4||Crown Castle||Zayo||Optus||PCCW Global|
|5||AT&T||Level 3 Communications||NextGen Group||Telstra|
|6||Cogent Communications||BT||AAPT||NTT Communications|
|9||Comcast||Orange Business Services||Zencross Connect||China Telecom|
- Central apparatus room
- Colocation center
- Disaster recovery
- Dynamic Infrastructure
- Electrical network
- Internet exchange point
- Internet hosting service
- Modular data center
- Network operations center
- Open Compute Project, by Facebook
- Server farm
- Server room
- Server Room Environment Monitoring System
- Server sprawl
- Sun Modular Datacenter
- Telecommunications network
- Utah Data Center
- Web hosting service
- "An Oregon Mill Town Learns to Love Facebook and Apple". The New York Times. March 6, 2018.
- "data center .. buildings and equipment
- "Google announces London cloud computing data centre". BBC.com. July 13, 2017.
- James Glanz (September 22, 2012). "Power, Pollution and the Internet". The New York Times. Retrieved 2012-09-25.
- Sparsh, Mittal,. "Power Management Techniques for Data Centers: A Survey".
- Angela Bartels (August 31, 2011). "Data Center Evolution: 1960 to 2000".
- Old large computer rooms that housed machines like the U.S. Army's ENIAC, which were developed pre-1960 (1945), were now referred to as 'data centers.'
- Til the early 60s, it was primarily the government that used computers, which were large mainframes housed in rooms that today we call datacenters.
- In the 1990s, Minicomputers, now called servers, were housed in the old computer rooms (now called data centers). "Server rooms" were built within company walls, co-located with low-cost networking equipment.
- Cynthia Harvey (July 10, 2017). "Data Center". Datamation.
- There was considerable construction of Data Centers during the early 2000s, in the period of expanding dot-com businesses.
- Cloud computing was supposed to be less expensive, yet ...
- "TIA-942 Certified Data Centers - Consultants - Auditors - TIA-942.org". www.tia-942.org.
- "Archived copy". Archived from the original on 2011-11-06. Retrieved 2011-11-07.
- "GR-3160 - Telecommunications Data Center - Telcordia". telecom-info.telcordia.com.
- Kasacavage, Victor (2002). Complete book of remote access: connectivity and security. The Auerbach Best Practices Series. CRC Press. p. 227. ISBN 0-8493-1253-1.
- Burkey, Roxanne E.; Breakfield, Charles V. (2000). Designing a total data solution: technology, implementation and deployment. Auerbach Best Practices. CRC Press. p. 24. ISBN 0-8493-0893-3.
- "Mukhar, Nicholas. "HP Updates Data Center Transformation Solutions," August 17, 2011".
- "Sperling, Ed. "Next-Generation Data Centers," Forbes, March 15. 2010". Forbes.com. Retrieved 2013-08-30.
- "IDC white paper, sponsored by Seagate" (PDF).
- Niccolai, James. "Data Centers Turn to Outsourcing to Meet Capacity Needs".
- "Tang, Helen. "Three Signs it's time to transform your data center," August 3, 2010, Data Center Knowledge".
- Miller, Rich. "Complexity: Growing Data Center Challenge," Data Center Knowledge, May 16, 2007
- Sims, David. "Carousel's Expert Walks Through Major Benefits of Virtualization," TMC Net, July 6, 2010
- Delahunty, Stephen (August 15, 2011). "The New urgency for Server Virtualization". InformationWeek. Archived from the original on 2012-04-02.
- "HVD: the cloud's silver lining" (PDF). Intrinsic Technology. Archived from the original (PDF) on 2012-10-02. Retrieved 2012-08-30.
- "Gartner: Virtualization Disrupts Server Vendors". 2 December 2008.
- "Ritter, Ted. Nemertes Research, "Securing the Data-Center Transformation Aligning Security and Data-Center Dynamics"".
- "Data Center and Server Room Standards".
CRAC (Computer Room Air Conditioner) Units: ... kit used ... to support ... Data Center Machine Room Floor.
- "computers in machine room".
... machine room is ...
- "IST Machine Room Uninterrupted Power Project".
Our two Computer Room Air Conditioners (CRACs) ... providing redundant ...
- (In this arena, only six companies were noted by Thomas, a financial data publisher) "Computer Room Flooring Water Detectors Suppliers". Thomas Publishing Company.
- "How to Design A Computer Room". Computerworld. June 7, 1982. p. 120.
Dorlen Products (Continued from Page 107) ... Liebert ...
- URL https://www.wateralert.com - manufacturer name: Doren Products
- both of which focus on raised floors; this is not their main business)
- a soup-to-nuts distributor/service company
- "Data Center Raised Floor History" (PDF).
- "Tips for Ordering Replacement Raised Floor Tiles".
- Hwaiyu Geng (2014). Data Center Handbook. ISBN 1118436636.
- Steven Spinazzola (2005). "HVAC: The Challenge And Benefits of Under Floor Air Distribution Systems". FacilitiesNet.com.
- "Telecommunications Infrastructure Standard for Data Centers". ihs.com. 2005-04-12. Retrieved 2017-02-28.
- "About Data Center". ESDS.co.in (ESDS Pvt. Ltd.).
- Patrick Thibodeau (April 12, 2016). "Envisioning a 65-story data center". Computerworld.
- "Google Container Datacenter Tour (video)".
- "Romonet Offers Predictive Modeling Tool For Data Center Planning". 29 June 2011.
- "BICSI News Magazine - May/June 2010". www.nxtbook.com.
- "Hedging Your Data Center Power".
- Clark, Jeffrey. "The Price of Data Center Availability—How much availability do you need?", Oct. 12, 2011, The Data Center Journal "Archived copy". Archived from the original on 2011-12-03. Retrieved 2012-02-08.
- "Five tips on selecting a data center location".
- Niles, Susan. "Standardization and Modularity in Data Center Physical Infrastructure," 2011, Schneider Electric, page 4. "Archived copy" (PDF). Archived from the original (PDF) on 2012-04-16. Retrieved 2012-02-08.
- "Strategies for the Containerized Data Center". 8 September 2011.
- Niccolai, James. "HP says prefab data center cuts costs in half".
- ASHRAE Technical Committee 9.9, Mission Critical Facilities, Technology Spaces and Electronic Equipment (2012). Thermal Guidelines for Data Processing Environments (3 ed.). American Society of Heating, Refrigerating and Air-Conditioning Engineers. ISBN 978-1936504-33-6.
- ServersCheck. "Best Practices for data center monitoring and server room monitoring". Retrieved 2016-10-07.
- "tw telecom and NYSERDA Announce Co-location Expansion". Reuters. 2009-09-14.
- "Air to air combat - indirect air cooling wars".
- "GR-2930 - NEBS: Raised Floor Requirements - Telcordia". telecom-info.telcordia.com.
- "NASA - metal whiskers research". NASA. Retrieved 2011-08-01.
- Detailed explanation of UPS topologies "EVALUATING THE ECONOMIC IMPACT OF UPS TECHNOLOGY" (PDF). Archived from the original (PDF) on 2010-11-22.
- "Data Center Fire Suppression Systems: What Facility Managers Should Consider".
- Sarah D. Scalet (2005-11-01). "19 Ways to Build Physical Security Into a Data Center". Csoonline.com. Retrieved 2013-08-30.
- Systems and methods for controlling an electronic lock for a remote device, 2016-08-01, retrieved 2018-04-25
- "Data Center Energy Consumption Trends". U.S. Department of Energy. Retrieved 2010-06-10.
- J. Koomey, C. Belady, M. Patterson, A. Santos, K.D. Lange: Assessing Trends Over Time in Performance, Costs, and Energy Use for Servers Released on the web August 17th, 2009.
- "Quick Start Guide to Increase Data Center Energy Efficiency" (PDF). U.S. Department of Energy. Archived from the original (PDF) on 2010-11-22. Retrieved 2010-06-10.
- Greenpeace (2017). "CLICKING CLEAN: WHO IS WINNING THE RACE TO BUILD A GREEN INTERNET" (PDF).
- Danilak, Radoslav. "Why Energy Is A Big And Rapidly Growing Problem For Data Centers". Forbes. Retrieved 2018-07-06.
- "Smart 2020: Enabling the low carbon economy in the information age" (PDF). The Climate Group for the Global e-Sustainability Initiative. Archived from the original (PDF) on 2011-07-28. Retrieved 2008-05-11.
- "Report to Congress on Server and Data Center Energy Efficiency" (PDF). U.S. Environmental Protection Agency ENERGY STAR Program.
- A calculation of data center electricity burden cited in the Report to Congress on Server and Data Center Energy Efficiency and electricity generation contributions to green house gas emissions published by the EPA in the Greenhouse Gas Emissions Inventory Report. Retrieved 2010-06-08.
- Canada Called Prime Real Estate for Massive Data Computers - Globe & Mail Retrieved June 29, 2011.
- Finland - First Choice for Siting Your Cloud Computing Data Center.. Retrieved 4 August 2010.
- "Stockholm sets sights on data center customers". Archived from the original on 19 August 2010. Retrieved 4 August 2010.
- In a world of rapidly increasing carbon emissions from the ICT industry, Norway offers a sustainable solution Retrieved 1 March 2016.
- Swiss Carbon-Neutral Servers Hit the Cloud.. Retrieved 4 August 2010.
- Katrice R. Jalbuena (October 15, 2010). "Green business news". EcoSeed. Archived from the original on 2016-06-18. Retrieved 2010-11-11.
- "Data Center Energy Forecast" (PDF). Silicon Valley Leadership Group.
- "Efficiency: How we do it – Data centers". Google. Retrieved 2015-01-19.
- Commentary on introduction of Energy Star for Data Centers "Introducing EPA ENERGY STAR for Data Centers". Jack Pouchet. 2010-09-27. Archived from the original (Web site) on 2010-09-25. Retrieved 2010-09-27.
- "EU Code of Conduct for Data Centres". iet.jrc.ec.europa.eu. Retrieved 2013-08-30.
- "UNICOM Global :: Home" (PDF). www.gtsi.com.
- "IEEE Xplore Full-Text PDF:". ieeexplore.ieee.org.
- Cosmano, Joe (2009), Choosing a Data Center (PDF), Disaster Recovery Journal, retrieved 2012-07-21
- "HP's Green Data Center Portfolio Keeps Growing - InternetNews". www.internetnews.com.
- Inc. staff (2010), How to Choose a Data Center, retrieved 2012-07-21
- "Siranosian, Kathryn. "HP Shows Companies How to Integrate Energy Management and Carbon Reduction," TriplePundit, April 5, 2011".
- "Architectural Principles for Energy-Aware Internet-Scale Applications - IEEE Journals & Magazine". ieeexplore.ieee.org.
- Bullock, Michael. "Computation Fluid Dynamics - Hot topic at Data Center World," Transitional Data Services, March 18, 2010. Archived January 3, 2012, at the Wayback Machine.
- "Bouley, Dennis (editor). "Impact of Virtualization on Data Center Physical Infrastructure," The Green grid, 2010" (PDF).
- "HP Thermal Zone Mapping plots data center hot spots".
- "Fjord-cooled DC in Norway claims to be greenest". Retrieved 23 December 2011.
- Noormohammadpour, Mohammad; Raghavendra, Cauligi (16 July 2018). "Datacenter Traffic Control: Understanding Techniques and Tradeoffs". Communications Surveys & Tutorials, IEEE. 20 (2): 1492-1525.
- "Iron Mountain vs Amazon Glacier: Total Cost Analysis" (PDF).
- "Iron Mountain introduces cloud backup and management service". September 14, 2017.
- "Cloudscene Rankings: Top Data Centers & Service Providers Worldwide". Cloudscene.
|Wikimedia Commons has media related to Data centers.|
|Wikibooks has a book on the topic of: The Design and Organization of Data Centers|
|Look up data center in Wiktionary, the free dictionary.|
- Lawrence Berkeley Lab - Research, development, demonstration, and deployment of energy-efficient technologies and practices for data centers
- DC Power For Data Centers Of The Future - FAQ: 380VDC testing and demonstration at a Sun data center.
- White Paper - Property Taxes: The New Challenge for Data Centers
- The European Commission H2020 EURECA Data Centre Project - Data centre energy efficiency guidelines, extensive online training material, case studies/lectures (under events page), and tools.